What's special about these pvc adapters?
- Constructed of schedule 40 PVC, these couplings are perfect for placing your conduit underground for direct burial, or encasing it in concrete
- Allows you to join together cut pieces of conduit with the use of solvent
- Can be used without fear of deterioration above ground, even in direct sunlight; however it should not be exposed to physical damage
- Click for More Features
Cantex PVC Couplings can be used in conjunction with rigid non-metallic PVC to penetrate fire-walls and ceilings, but must be used with a firestop product to meet code.
Please Note: These products ship 3-4 weeks from ordering
|BTX-YD-RS232MX9F||DB9 Female Control Cable Kit: Includes 3ft 8-Pin Mini DIN cable, clamshell hood, and connector|
|BTX-TD-RS232MX9M||DB9 Male Control Cable Kit: Includes 3ft 8-Pin Mini DIN cable, clamshell hood, and connector|
|BTX-CA-MX35M||3.5mm Male Cable Mount|
|BTX-CD-MX915H||Hood for MaxBlox D-Subs|
|BTX-CD-MX915HH||Half-Hood for MaxBlox D-Subs|
|BTX-TD-MXSD||Screwdriver for MaxBlox Series|
- PVC conduit has an excellent range of temperatures, for versatility in many environments – it can be used from -4° to 122° F, and does not ignite until after 734° F
- PVC is safe and easy to use
- Meets all standards for: UL 651, NEMA TC-2 , NEMA TC-3 andNEC Article 352
- CSA Certified
- 1 year manufacturer’s warranty - PDF
Ideal for use with:
- Electrical Non-Metallic Conduit
Schedule 40 couplings with center stop
|PART #||SIZE||WIDTH||LENGTH||"ID"||"D"||PRICE / Unit|
|UL Standards||UL 651|
|UL Category Code||DWTT|
|NEC Article 352|
MANUALS & USER GUIDES -
Difference between Schedule 40 and Schedule 80 Conduit
The difference between Schedule 40 and Schedule 80 lies in the thickness of the wall of the piping. The Schedule 40 has a thinner wall than the Schedule 80 piping even when dealing with the same size pipe. Because the pipes are the same size on the outside, the difference lies in the interior. They will differ by inside diameter.
A 1" (25.4 mm) Schedule 40 pipe will have an outside diameter of 1.315" (33.4 mm) and an inside diameter of 1.029" (26.1 mm). A 1" (25.4 mm) Schedule 80 pipe will have an outside diameter of 1.315" (33.4 mm) and an inside diameter of 0.936" (23.8 mm).
They will look identical from the exterior. The reason for the difference is that thicker piping allows for larger pressure. Thinner piping and fittings however are less expensive typically.
Can you connect schedule 40 and schedule 80 2" and 4" PVC conduits together in a run?
Schedule 40 and 80 can be connected with the use of couplings. The inside diameter of the spigot of the schedule 80 conduit should be reamed to allow a smooth transition from the 40 to the 80.
What is the burn time for the non-metallic or PVC conduit?
PVC Schedule 40 and Electrical Nonmetallic Tubing (ENT) do not have a "burn times". Both of these products have been evaluated and approved for use within a two-hour firewall assembly. Some would say the product has a "two hour rating".
Did you know that we can give you a quote for most of our products, including shipping?
You can also call us toll free 866-222-0030
Questions & Answers
Do you have any questions about this product?
Let our experts and customers resolve all your doubts